In accordance with The Regulatory Reform (Fire Safety) Order (RRO), Approved Document B , BS 9999 and BS 5839 part 1 all modern, complex buildings fire detection and fire suppression systems should be designed in association with a fire strategy and fire prevention risk assessment.
The Fire Risk Assessment will determine and record the building hazards and risks and the fire strategy will determine the interactions and interconnections of the various building fire alarm systems with other critical building services to mitigate the risk, such as air handling systems, fire dampers, lift systems, security control systems, fire doors, remote monitoring and with the sounders or voice alarm speakers, and beacons and visual alarm devices that also form part of the fire alarm system.
What is the purpose of Cause & Effect Testing?
The purpose of cause and effect analysis is to document the current Cause and Effect of the fire alarm system within the premises, so that it is understood how the alarm system operates.
The fire alarm systems triggers or inputs – call points, smoke/heat detectors, aspirating detectors, sprinkler flow/pressure switches – are the Cause, and the outputs or Effects are the shutting down of air supplies, opening of vents, closure of dampers, shutting down of fuel supplies, unlocking of access controlled doors, closing of held open fire doors, signalling to fire authorities, phased evacuation operation of sounders and visual indicators or voice alarm speakers.
How often should Cause & Effect Testing be undertaken?
BS 5839-1 section 45 regarding Inspection and Testing states that annually the Cause and Effects should be tested and in particular sites with multiple cause and effects operations more detailed testing should be undertaken.
In order to prove the correct fire strategy operation it is essential that the tests are undertaken and checked as an end to end test, not just a test to fire alarm interface units or relays that provide the signalling mechanism to the critical building systems.
It is important that the fire alarm system service provider can prepare a cause and effect testing matrix that is used to prove end to end function tests from the cause of call points and smoke detectors so that the responsible person can witness the correct effects operation on the associated fire strategy building services systems.
The site inspection focuses on the following items:
- Condition report of the current fire alarm detection systems, including all linked systems.
- Confirmation of the current cause and effect of the system.
- Confirm the current fire strategy to the building and if any changes need to be made.
- Make recommendation for system upgrades or amendments to comply with current standards.
Full visibility of activation locations
Full audit trial of false alarm history
Continuity across the property with regards to equipment and procedures
Reduced need for multiple residents, customers or clients evacuating at one time.
Sounders not being activated throughout property and causing disruption to occupants.
In some case systems having the ability to remote connect to systems for reporting purposes and interrogation